Pet and Household care manafacturer
Hot well located above an industrial boiler
- The tank was leaking from several places.
- The tank was severely corroded and had very deep pitting or cratering.
- Due to its high temperature, the water seeping from the tank was potentially hazardous.
- It was located in a small room, approximately 3m above a boiler.
- As the boiler was operational throughout the project, the entrance temperature reached 40°C.
- Numerous hot pipes were located near the manway entrance.
- A complex array of internal steelwork made working conditions difficult.
- An external plate at been welded to the underside of the tank in attempt to stem the leaks.
- Due to the tight positioning of the tank, replacing it would be costly and time consuming.
The internal surfaces of the tank were extensively blast cleaned with abrasive grit to SA2.5 to remove rust, dust, scale and other deposits. Having cleaned the tank, a primer coat of high temperature resistant resin was applied and a total of seventeen holes and deep craters that were close to perforation were filled using a special resin based surface repair system. The floor of the tank was reinforced with a screed coating. A high temperature resistant main coat was applied in multiple layers to ensure complete coverage. We rigorously tested the tank linings throughout each process for coating thickness and absence of holes in the new lining.
By restoring the tank lining, we were able to bring the tank
back into optimum production and extend its lifespan by ten to fifteen years,
subject to regular inspections and general maintenance. The project was
completed on time as projected and the onsite engineer confirmed the expense of
lining the existing tank cost 10% of the price of full tank replacement.